How to install this product
Fire protection for KERDI-LINE-V 50 G2 with Schlüter-KERDI-LINE-BS /-ZBS
As specified by approval number Z-19.17-1719, the system components prevent the spread of fire to another floor level. The fire protection insert (Art no. KL BS) is placed within the drain body of the linear drainage set KERDI-LINE-V 50 G2.
Installing the fire protection insert KL BS:
- Set the fire protection insert in place.
- Then insert the clamping ring, using the supplied lubricant.
In conjunction with the conduit gasket (Art no. KD ZBS), which can optionally be fitted into the core hole (ø 160 mm), the source material contained in the fire protection insert foams up at temperatures of about 150 C and above to safely prevent the spread of heat, fire and smoke for a fire resistance duration R120, R90, R60 or R30 (depending on the ceiling structure).
The fire protection function of the conduit gasket KD ZBS only applies in conjunction with the fire protection insert KL BS!
As an alternative, the drain body must be encased in concrete or fully incorporated in the solid ceiling with an MG III cement mortar.